Enclosure Product Specs for Engineers
Thank you for your recently attending a Fibox presentation.
To save you time, Fibox has prepared ready to copy text that you may easily add into your project document, or download a pdf version for your files.
If you have any questions please feel free to contact Fibox directly for more information.
FIBOX – ARCA JIC HINGED COVER NONMETALLIC ENCLOSURES – PRODUCT SPECIFICATIONS
A. Comply with UL 50, “Cabinets and enclosures” and NEMA Type 1, 3, 3s, 4, 4x, 6, 6p, 12 and 13.
B. Construction: Polycarbonate/Plastic
C. The body shall be manufactured from a high-impact, corrosion resistant material; UV stabilized for outdoor use, and comply with UL-94 minimum V-0 requirements.
D. Cover shall be manufactured from a high-impact, corrosion resistant material, UV stabilized for outdoor use, and comply with UL-94 minimum V-0 requirements.
E. cover shall properties through overall long term temperature range of -40° F to 175°F and short term temperature range of -40°F to 284°F.
F. Body and cover shall be free of rough corners, sharp edges or burrs.
G. Cover screws (10-32) shall be captive slotted stainless steel (type 304) fillister head.
H. Door: Continuous hinge; stainless steel lockable latch unless otherwise indicated, formed-in-place (FIP) gasket.
I. Mounting Panel: Provide painted a removable internal mounting panel for component installation.
J. 10-32 or ¼-20(depending on size) brass threaded inserts for mounting panel & mounting feet.
K. Mounting feet shall be removable.
L. Back panel mounting means shall accept standard size back panels.
M. shall be listed and as defined in UL 50, by a qualified testing agency, and marked for intended location and application.